XP6-MA Notifier six-zone interface module provides an interface between the intelligent alarm system and a two-wire conventional detection zone. A common SLC input is used for all modules, and the initiating device circuits share a common external supervisory supply and ground. Otherwise, each module operates independently from the others.
Six addressable Class B or three addressable Class A initiating device circuits.
Removable 12 AWG (3.1 mm²) to 18 AWG (0.78 mm²) plugin terminal blocks.
Status indicators for each point.
Up to two unused addresses may be disabled.
Rotary address switches.
Class A or Class B operation.
FlashScan® or CLIP operation.
Mount one or two modules in a BB-XP cabinet (optional).
Mount up to six modules on a CHS-6 chassis in a CAB-3 Series, CAB-4 Series, BB-25 cabinet (optional), or EQ Cabinet Series.
Mounting hardware included.
The first module is addressed from 01 to 154 while the remaining modules are automatically assigned to the next five higher addresses. Provisions are included for disabling a maximum of two unused modules. All two-wire detectors being monitored must be two-wire-compatibility-listed with the modules. The XP6-MA transmits the status of a zone of two-wire detectors to the fire alarm control panel. Status conditions are reported as normal, open, or alarm.
The interface module supervises the zone of detectors and the connection of the external power supply. Each XP6-MA module has panel-controlled bicolor LED indicators. The panel can cause the LEDs to blink, latch on, or latch off.